1A. Prepare holes in the concrete chamber according to the spacing guidelines. (Advice PDF File: Furukawa Long Bell Mouth Installation Procedure) 1B. Alternatively, create a single opening in the chamber to house the entire EFLEX Square sack. (Advice PDF File: Furukawa Long Bell Mouth Installation Procedure) 2. Cover the single opening on the inside of the chamber with a plate (or similar) and hold it in place with a wooden block/ spacer (or similar), while work is carried out. 3. Connect the Long Bell Mouth to EFLEX Square:
Remove the temporary cap from the male connector of EFLEX Square.
Apply lubrication to the rubber seal on the male connector and the inside of the female connector of the Long Bell Mouths.
Ensure the connectors are free from dirt and debris and insert the male connector into the Long Bell Mouth in a straight line.
Check that the connection is secure by pulling in the opposite direction by hand.
4. Remove the paper backing from the tape seal on the Mouth and place in position. 5. Position remaining Mouth/ EFLEX Square units ensuring the of the Mouth is touching the plate on the inside of the chamber. 6. Assemble a form and pour in concrete. Allow to set before disassembling.
System & Accessories
For more information on the Furukawa Long Bell Mouth, please advise PDF Files below., 277670
FREE Technical Advisory Service
E-Tech Components UK Ltd maintains a free technical advisory service. Contact us for enquiries concerning this and all other products: +44 (0) 1744 762 929
Find out more about our products or becoming a supplier